When product vapor pressure is greater than 0.5 psia (more in some states) but less than 11.1 psia, the U.S. Environmental Protection Agency permits the use of a floating-roof as the primary means of vapor control from the storage tank. Floating-roof tanks are not intended for all products. In general, they are not suitable for applications in which the products have not been stabilized (vapors removed). The goal with all floating-roof tanks is to provide safe, efficient storage of volatile products with minimum vapor loss to the environment. Design requirements for external floating roofs are provided in Appendix C of the API Standard 650.